KIT Underfloor electric water heating system 1400W, XL-pipe 35m, thermostat
- Underfloor electric hot water heating XL-pipe – 1400W, 230V, 40W/m, pipe length 35m, diameter 20mm. It has 5 years manufacturer warranty.
- Power distribution box
- Connection terminals
- Thermostat – your choice:
- junction box
- flexible conduit 3м
- Easy step-by-step installation guide & Warranty Card
Heating X-L PIPE
An innovative heating technology which improves heating efficiency using special heat medium and expansion pressure by heating the heating wire in a closed X-L pipe without a boiler or circulating motor which is the medium for floor heating.
- It can be used as primary heating or additional heating source
- Electric hot water heating system XL-pipe to install in cement screed is used for underfloor heating of dry rooms with tiles, natural stone, laminate, wood floor, carpet finishing
- Does not require boiler room, having advantage in utilization of space
- Does not require facility piping, saving construction cost and construction period
- Easy control through the thermostat
- Electric energy is turned into heat and used for 100% room heating
- Saves heat cost by over 70% for the area of the same size compared to oil heating
- Heat medium filled in piping and heat storage effect of plastered layer enable heating for a long time using a small amount of energy
- Our shielding facility is free of electromagnetic waves and harmless to human body
Installation XL pipeMaterials: 1. Heating system X-L PIPE 2. Power distribution box
Service and maintenance are easy to carry out after the installation3. Temperature controller – thermostat
The temperature controller shall be able to set the maximum limit. The temperature sensor shall have the functions of not only temperature sensing,but also leakage prevention and excessive temperature rise.4. Accessories:
Silver coated insulation sheets – 3 mm, reinforcing steel net #20 (metal or plastic) for fixation of X-L pipe on it, tile supports and fixing pins (U-pins).Preparation: Make sure X-L tube is filled with liquid. Check the insulation condition. More than 50mm of bubble concrete or more than 30mm of compressed styrofoam should be laid. Installation: 1. Insulation – once you have covered the floor with foam concrete or Styrofoam, place insulation sheets with silver side up on it. electrical hot water heating system x-l pipe_insulation 2. Reinforcing steel net placement – place reinforcing steel net and fix it.electrical hot water heating system x-l pipe – insulation 2 3. Installation of power distribution box
- The power distribution box shall be installed horizontally. The top of the power distribution box shall be at a level with the height of the mortar.
- The power distribution box shall be installed allowing enough space between it and the wall so that the cover of the power distribution box can be easily opened after completing its installation.
- The power distribution box shall be firmly fixed so that it does not get loose.
4. Installation of energy-saving electric hot water tube
- Bending shall be done as follows. The products should not be folded or twisted. The hot water tubes should maintain level
- Bending length: 800mm / Bending diameter: 220mm
- They shall be fixed with coil supports (clip bars) and fixing pins (U pins) (when the floor is finished with bubble concrete)
- Fixing pins for straight tubes around coils shall be used at a distance of every 8 meters and those for other straight tubes shall be used at a distance of 0.5 meters
- There are more than 2 places for 90˚ bended tubes. Refer to the design drawings and fix them firmly so that coils do not get lifted and loose
- In case the floor is finished with insulation materials (styrofoam), lay wire mesh and then install energy-saving electric hot water tubes. The tubes shall be tightly fixed to wire mesh with cable ties so that they may not be pushed while mortar coating
- Energy-saving electric hot water tubes shall be installed 250mm ~ 300mm away from the wall.
The lead wires for energy-saving electric hot water tubes shall be thicker than those specified on the drawings. They shall be connected to the output terminals of the temperature controller in parallel6. Installation of temperature sensor
The temperature sensor and the excessive temperature rise protector shall be inserted into the bellows tubes, installed 20mm away from energy-saving electric hot water tubes, and fixed on the floor
The power distribution box shall be sealed with OPP tapes or blue tapes to protect it from moisture while mortar coating.
- Be careful not to block the power distribution box while mortar coating
- Mortar thickness: 30~40mm – laminat, multilayer parquet, linoleum, tiles, Ondol (Korean floor heating system) floor, 20mm – marble
9. Installation of temperature controller
- The temperature controller shall be installed vertically and horizontally and the temperature sensor shall be properly connected to prevent malfunction
- The temperature controller (individual heating system) shall be installed at the height of 1.2 meters above the floor so that it can not be obstructed by furniture. If it must be installed close to an electric switch, the horizontal distance between the switch and the controller shall be more than 200mm
- After the mortar is completely dried up, check if there is any electrical short in the wiring on the side of outputs and then supply electrical power
- Check if the temperature controller works properly at the set value. (A space is created between the hot water tube and the mortar)
- Using a load (current) measuring instrument, check if the electrical output is correct in accordance with its specification
- Check if the temperature controller is properly set
INSTALLATION XL PIPE download this link
If you have any questions do not hesitate to contact.
IMPORTANT: Our delivery service requires phone number of a recepient, thus please write us a message with your phone number so we could dispatch your order in time.